The electrical supplies at Makespace are very confusing, there are at least five distribution boards supplying the circuits in Makespace. The sockets in Makespace are not protected by RCDs; there are plans to address this in the near future.
Over the 2012 Christmas break, a quick survey was done and the following was found:
In the class room, circuits are fed from a distribution board located outside of Makespace and were not checked.
In the corridor, circuits are fed from a distribution board located outside of Makespace and was not checked.
The main workshop circuits are fed from the two distribution boards located in the workshop. The left-hand board supplies power for the lighting and sockets in the main workshop (lights only), kitchen, quiet room, store room and the right-hand distribution board. The sockets in the main workshop are fed from the right-hand distribution board. The right hand distribution board circuits are protected via an electrical contactor; when any of the red emergency stop buttons in the workshop are operated, the supply to the right hand board is isolated, and therefore any circuits supplied from it will also be isolated.
The secure workshop lights are fed from a distribution board located outside of Makespace and was not checked.
The sockets in the secure workshop are fed from the distribution board located in the secure workshop. The distribution board is protected via an electrical contactor; when any of the red emergency stop buttons in the secure workshop are operated, the supply to the distribution board is isolated, and therefore any circuits supplied from it will also be isolated. The sockets in the secure workshop are split into three circuits. A 32A ring main, 16A circuit control with a switched spur, and a 10A high level socket.
The office lights and sockets are fed from its own distribution board. This distribution board is over 15 years old; since the office space is not going to be used for making, I don't see the need for the sockets to be RCD protected as long as the equipment used within the office is only IT equipment.
The kitchen lights and power is fed from the Main Workshop left-hand distribution board.
The quiet room lights and power is fed from the Main Workshop left-hand distribution board. The low level and high level sockets are fed from different circuits.
The store room's sockets are fed from the Main Workshop left-hand distribution board. The lights are fed from a distribution board outside of Makespace.
If you find a fault with any part of the electrical system at Makespace, stop using it, label it as faulty and please log it via electrics <at> makespace.org (Not yet set up), and inform Brian Corteil aka 'BrianC', one of the directors, or a trusted member if available.
|Date||Fault||Fault location||Reported by||Reported To||Actioned||Completed||Comments|
|01/01/2013||Example: Tube blown||Store||A Body||Brian Corteil||02/01/2013||Yes||replaced tube|
Please list your requests here.
- For example: 4 new sockets for the new metal working bench in the secure workshop --Brian Corteil 16:01, 5 January 2013 (UTC)